HDPE pipe with blue external wall and black internal wall for underground networks and pressurized water.
RC pipes (Resistant to Crack) for pressurized fluids supply, made of PE100 resins with high resistance to slow crack growth, FULLY comply with the standards used in the European market. The features of RC resins are much higher than those required by traditional standards, resulting in mechanical and durability performances that meet the modern needs of operators and installers; moreover, they turn out to be the most appropriate for underground laying “trenchless” techniques as well as laying “without sand bedding” as specified in S.T. PAS 1075. Pipes produced with PE100 RC resins are proposed with Piip / c quality mark issued by the Italian Institute of Plastics (IIP) in the technical specification (Mod. 1.1 / 14 – Rev. 0 and Rev. 1) FOR PIPE FOR PRESSURIZED FLUIDS SUPPLY MADE OF PE 100 “RESISTANT TO CRACK” (PE100- RC).
:: reduction / elimination of maintenance
:: lower network management costs
:: higher service efficiency
:: less problems for the final users
:: longer life-span
:: pipes completely compliant to the various standards
:: correspondent to all types of connections
:: suitable for NO-Dig
:: more resistant to chemical agents
:: advantageous cost/benefit rapport
TECHNICAL SPECIFICATION (type2)
RC pipe (Resistant to Crack) of TYPE2 for pressurized water underground networks, made of High Density Polyethylene PE100 resin with high resistance to slow crack growth, pigmented and stabilized in granules at source and distributed on two layers: the internal layer in black constituting 90% of the total thickness and the external in blue constituting the 10% of the total thickness, fully complying with UNI EN 12201, ISO 4427, UNI EN ISO 15494 and technical specification DIN PAS 1075, both included in the “technical specification IIP MOD. 1.1/14 – Rev. 0″ with issue of Piip/C quality mark. Pipe samples shall have successfully passed all the tests required by the reference standards above, including the PLT (Point Loading Test) for resistance to slow crack growth > 8760 h. The marking shall report in full the code of the raw material used for the production of the pipe, as well as other elements required by the reference standards.